|Brand||GK Infra Engineers|
|Usage||Industrial up to 5 chillers|
|Cleaning System Type||Multi chillers|
|Phase||3 Phase + Neutral|
Sponge balls resting in the Ball Collector are periodically injected to the condenser cooling water inlet pipe by the operation of a booster pump and control valves mounted on a Skid.
These balls travel with normal condenser water flow in the condenser and pass through the tubes. While passing through the tubes ball carries away all the Soft Scales and deposits accumulated on the inner surface of the tubes and so keep the tubes continuously clean. The balls come out of the condenser from the outlet side of the condenser to and get trapped in the Ball Trap, while hot return water goes to the cooling tower.
Ball trap is installed on the cooling water return pipe. Once all the balls are out of the condenser and get trapped, these are pulled back and washed in the Ball Collector by operation of the same booster pump and control valves mounted on a Skid. The cycle is repeated every 10 to 30 mins to ensure 100% tubes get cleaned.
The operation is Fully Automatic Controlled through PLC Controller with NO Human intervention.